Coal Fired Steam Boiler SZL Series
Brief:Water-fire tube structure
Rated Capacity: 1 ton/hr-20 ton/hr 0.7MW-10.5MW
Rated working pressure:0.7/1.0/1.25/1.6/3.82Mpa 6bar
Coal Fired Steam Boiler SZL Series
Model NO.: SZL
Structure: Water Tube
Water Circulation: Natural Circulation
Pressure: Low Pressure
Burning Style: Grate Furnace
Water Temperature: 95-130 Degree Centigrade
Place Style: Horizontal
Specification: 2.8MW, 4.2MW, 5.6MW, 7MW, 10.5MW, 14MW, 17.5MW
HS Code: 8402120090
Function: Steam Boilers
Installation: Assembled Boiler
Media: Hot Water
Drum Placement: Horizontal Boiler
Manufacturing Level: A
Water Pressure: 0.7-1.25MPa
Heat Efficiency: Above 80%
Gas Flow Type: Water Tube
Transport Package: Nude
Origin: Qingdao, China
SZL series hot water boiler is a kind of horizontal, double-drum, water tube, chain grate boiler. There are two drums up and down: Steam drum and water drum. The front of steam drum and two-side water tubes walls compose radiation heating area. The convection tube bundles between the back of steam drum and the whole water drum compose the convection heating area. The economizer is arranged at the back of the boiler. In the economizer, the soft water is heated by hot smoke. Then the hot soft water goes into the boiler. It makes use of the hot smoke's heat and saves more fuel. The steam comes out of boiler to go into the steam distributor, which will distribute the steam for different equipments. There are two kinds of cyclones for your choice: Multi-tubular cyclone and water-film cyclone. The dust removal efficiency of both cyclones is up to 95%. While the SOx and NOx removal efficiency for the sencond one is up to 98%.
3.1 After simplifying the water-cycle route, we can reduce the water-cycle resistance, raise ascending Tube velocity, improve the reliability of the water cycle and ensure a safe and stable operation.
3.2 Design enough heating surface, which makes more heat from fuel absorbed. Flue gas temperature Is about 170o C.
3.3 Reasonably designing front and back arch to improve the temperature in the furnace, we also Rengthen the disturbance of smoke in the high-temperature region. That reduces heat loss and Fly-ash loss as a result of incomplete combustion.
3.4 We adopt light chain grate. It is easy to operate and convenient to maintain. That makes sure that the Fuel is burned fully.
3.5 Our boilers have a large convection heating surface, a stable performance and even a long time Overload work. What's more, we design the convection tube bundles in alternate permutation instead Of in-line arrangement. All of those make our boilers can absolutely have a high heat efficiency.
3.6 Through taking above measures, thermal efficiency of each specification boiler is more than 80%, And is higher than national standard.
3.7 We design double-side air inlet and independent air plenum. And at the exit of furnace we set up a Smoke separation device by inertia, which makes the original discharging dust concentration lower Than 1800mg/Nm3. Our efficient water film dust scrubbing dust collector makes sure the dust Removal efficiency up to 95% and SOx and NOx removal efficiency up to 98%. These measures can Meet all the demands and standards of environmental protection in the world.
3.8 Compact structure (except the 4t/h steam boiler, the others are assembled at site). We design a Compact structure, which can reduce the installation workload at site and shorten 2/3 of installation Period.
3.9 We enlarge the diameter of steam drum to improve the water-steam separation device. So that we Can ensure the steam of good quality.
3.10 High automatization and easy operation. With our home-made ECC, we can achieve automatic feeding water, alarm and safety interlock of water level, safety interlock of air blower and induced draft fan, etc.