Place of origin:shandong China
Model Number: ISO Type
Size：from 1t to 40t
Fuel:natural gas、liquefied petroleum gas ( LPG )、city gas
ated capacity :1-20ton/hr
Rated working pressure :0.7/1.0/1.25/1.6/3.82 Mpa
7bar /10bar /13 bar
101psi /145 psi
Application:Rice mill ,chemical industry ,textile mill ,food processing and others.
All important components and key parts of the high efficiency gas steam boiler produced in our factory are equipped with fully automatic argon arc welding technology, the welding quality is really good. In order to enhance the competitiveness of our boilers in the market, our factory is equipped with a continuous water supply and multi-level alarm protection for boilers. In addition, the high efficiency gas steam boiler can be adjusted as needed to form an oxidizing atmosphere and a reducing atmosphere. For the supply of boiler combustion raw materials, our boilers can be burned with readily available raw materials made of solid materials. In order to meet the needs of environmental protection in most regions at home and abroad, our designers through the experience of nearly 40 years to design a set of equipment to improve efficiency.
high efficiency gas steam boiler emergency shutdown
When the boiler is running, one of the following conditions should be immediately shut down:
1、The high efficiency gas steam boiler water level is lower than the visible edge of the lower part of the water table, increasing water supply and other measures, but the water level continues to decline;
2、The high efficiency gas steam boiler water level exceeds the highest Water level (full of water) can not be seen after the water level;
3、 water pump failure or failure of the water supply system, not to the boiler water;
4、 high efficiency gas steam boiler components damaged, endangering the safety of operational staff;
5、other abnormal situation endanger the safe operation of the boiler. In case of power failure, water and other emergencies should take timely measures. If you can not solve it, you should promptly report to the company. It is forbidden to repair the pressurized components of boilers under the condition of high pressure or the temperature of the boiler water to prevent the steam and water from being sprayed and wounded. Equipment under repair, to hang warning signs.